View and Download Hach Sc E instrument manual online. Analysis System. Sc E Measuring Instruments pdf manual download. Hach Sc Controller User Manual – Download as PDF File .pdf), Text File .txt) or read online. Hach Sc Controller User Manual . Hach Company, – .. 37 W with 25 W sensor/network card load 24 VDCpowered sc model: 24 VDC.
|Published (Last):||28 July 2010|
|PDF File Size:||15.12 Mb|
|ePub File Size:||18.79 Mb|
|Price:||Free* [*Free Regsitration Required]|
Wet Verification System Startup 5. Pay attention to all danger and caution statements. Controller Display Features Operation 4.
The keypad consists of the eight keys described in Table 7. Section 5 System Startup 5. Page 12 Installation 3. Table of Contents Section 1 Specifications Page 31 Operation 4.
Hex nut, M6 4Cat. Page 10 General Information hac. Open the controller cover. Page 14 Installation 3. System Startup Two types of verifications are offered. Page 26 Installation 3. Fuses F1 and F2.
Hach sc100 1720E Instrument Manual
Follow the appropriate wiring instructions per the purchased model. Page 71 Index Sample Line Installation The controller display shows the current reading plus a secondary measurement such as temperature if connected to a single sensor, or two readings with their corresponding secondary measurement readings when two sensors are connected.
Page 34 Operation 4. Failed fuses are an indication that hacy equipment problem could exist. Troubleshooting Troubleshooting Table 11 presents sensor warnings displayed in the Event Log, possible causes, and corrective actions.
Pan head screw, M6 x 1,0 x mm 4Cat. Page 25 Installation 4. Table of Contents Section 1 Specifications Push in and turn to secure the connection.
Page 72 Visit http: Table 1 Turbidimeter Specifications Nephelometric light scatter at 90 degrees relative to the incident light beam. To locate the representative nearest you, send e-mail to intl hach. Section 6 Replacement Parts 6.
Rinse with deionized water before calibrating. Drain body and clean the body and bubble trap. The passcode is factory set to sc the five digits must be followed by a space to remove the trailing asterisk. Relay loads must be resistive. To hold the output until released: All configuration settings and calibrations can be changed.
Page 46 Warranty, liability and complaints 7.
Hach-Lange SC User Manual | 58 pages
Controller Dimension Illustrations Installation 3. Disconnect and remove the existing wires between the quick connect and terminal block J5, see Figure 21 on page 4. Page 20 Sc10 3.
This is the default setting. Page 58 Index Page 51 Modbus Protocol Table 9: Installation Electrical Installation High-voltage wiring for the controller is conducted behind the high voltage DANGER The instrument must be installed barrier in the controller enclosure.
Page 38 Operation 4.
Hach-Lange SC 100 User Manual
Mounting The Controller Installation 3. Pull the lamp leads and connector through the hole sc1000 the lamp housing. Table of Contents Section 5 System Startup Pass the cable through conduit and a conduit hub or a strain relief fitting and an available access hole in the controller enclosure. The barrier must remain in place unless a by qualified technical personnel qualified installation technician is installing wiring for power, alarms, or relays.
Customize the outputs using the table in section 4. Pipe vertical or horizontal 5.
Supplied mounting hardware is shown in Figure 6, Figure 7, and Figure 8. Page 18 Installation 3.